Commercial Gas Services
To assure that the correct size gas service, meter, and regulator will be installed, the customer or the HVAC/mechanical contractor must supply Wilson Energy with the total BTUH load and the system delivery pressure. Please e-mail the BTUs per appliance and the delivery pressure required to email@example.com or fax to (252) 399.2191 when applying for service. At that time, the size and placement of the service will be determined.
Services CAN NOT be installed:
- Inside fenced areas.
- Anywhere subject to damage.
- Within three feet of openings in buildings, including crawl spaces, windows and doors. A service can be installed within three feet of an existing vent if the vent has been permanently closed.
- Within three feet of any ignition source, including electrical, television or telephone connections; electric meters; and furnaces.
Once the gas service has been installed, either the contractor or the owner/customer must call the Wilson Energy office at (252) 399.2432 to have the meter set. Once the meter has been set and the piping has passed inspection, the owner/customer must call Customer Service at (252) 399.2162 to have the gas service turned on. The gas meter will not be set until requested.